How to extend the service life of stainless steel submersible pumps?
Posted by Admin | 14 Dec
The efficient use of stainless steel submersible pumps is inseparable from the maintenance of the staff, but often many users will ignore this point, resulting in frequent equipment failures, and the loss is not worth the loss. In order to make your future use more smooth, please check the cables, switches, electric shock protectors, etc. before using the stainless steel submersible pump. The switches and other electrical appliances should be working properly and the cables should not be damaged. Pay attention to carefully identify the cables because of yellow and green. The two-color wire is the ground wire to prevent leakage and electric shock accidents.
At regular intervals, check the insulation resistance of the submersible pump before use. It should not be less than 0.5MΩ. If it does not meet the requirements, it must be dried. Check the drain hole and oil drain hole regularly, and tighten if there is no abnormality.
After the stainless steel submersible pump has been working for 300 hours, it must be checked for water discharge. If the discharged water or oil-water mixture is less than 25mL, it can be used continuously, otherwise, check whether the casing and rubber sealing ring are damaged.
Because the stainless steel submersible pump should be used in water under normal conditions, it should not exceed 5 minutes to prevent the motor from heating and burning. The maintenance of stainless steel submersible pumps can not only ensure the efficient work of the equipment, but also extend the service life of the equipment and reduce the operating cost of the enterprise. Why not do it.